Give us a call! 405-912-5900
Since Interstate Heating and Air Conditioning was founded in 2002, Meeker, OK knew they could rely on us for professional and pleasant service.
Curious about what your Meeker, OK are saying about us? Check out our reviews below for real experiences.
for Meeker, OK
Our Reviews by City
MITCH - Meeker, OK
Came as soon as available and the usual great service. Thanks Brandon!
Performed silver club heater maintenance. Filter was clogged and causing limit switches on elements to trip. Replace filter. Test capacitor and motor amp draw. Amp draw in range. Test sequencers, relays in limits. All are in working order. Amp draw to 1 side is slightly elevated but in working order. Breaker could be in a little better condition. Spoke to customer about it. Customer will replace breaker if needed. Unit is putting out 120f heat. Heater is working properly at this time.
Arrived to service call we replaced ductwork and plenum recently. Customer was due to have free air flow adjustment. Performed adjustments to area that customer had concerns. The adjusted areas where kitchen and living area. Opened living area all the way and dining halfway. Customer stated airflow was good. Also showed customer how to adjust airflow for any adjustment needed in future. Airflow in all areas is strong and system is heating well at this time. No charges to customer
Replace ductwork with correct sized ducts and metal plenum
Performed duct inspection gave estimate to replace ducts with correct sized duct for 4 ton system complete with metal plenum. Will apply todayâ€™s balance towards repairs if customer chooses to replace ducts.
Arrived to no cool service call performed system evaluation. Found system frozen up solid. Unthawed unit. Found system low on r22 refrigerant. Spoke to customer at this time customer chose to add refrigerant to system. With customer approval I added 1lb 13 oz to system. System is cooling at this time. System is starting to show signs of age if becomes low on refrigerant in near future suggest leak repair or consider system replacement due to age and condition. System is cooling at this time.
I arrived for a non member cooling to much call. I first inspected the indoor furnace and found the systems to be running with the thermostat to be calling for cooling. I removed the doors to the furnace and the door switch turned the system off. I turned the thermostat to the off position and supplied powerful back to the furniture. I cycled the system four times from the thermostat and found the system to shut off and turn on when told to. I could not inspect the evaporator coil due to the evaporator box is installed in a plywood and metal box around the evaporator coil box. I recommend to have the system repaired before any further issue present itâ€™s self in the future this system is 26 years old. I inspected the condenser and found the systems to be running and the high side schrader core to be broken and was leaking refegerant once I remove the cap. I tried to remove and replaced the schrader core but it will not remove. I tightened the cap back down on the high side king valve
Arrived to service call performed system evaluation. Customer changes filters regularly. Condenser clean. Tested capacitor and compressor amp draw. Refrigerant levels in range. Amp draw on condenser motor was over amping and from the sounds the problem customer was describing sounds like defrost board was intermittently sticking. Customer stated system was on heat and condenser was running but fan was not and top was burning hot. As a precaution i replaced both parts. System heating and cooling at time.
I came out for a no cool. I checked the system over and found the condenser fan not running. One of the wires that control the universal fan direction had broken loose. With approval I repaired the wire and secured it, so it stays out of the fan blade. I washed the condenser coil as well. I cycled the ac and checked all operations. The ac was a bit undercharged. Sheâ€™s aware the system has a leak. I added 1.4lbs or r410a and set the SH to the required 30. All working at this time.
Replace blower motor to Goodman air conditioner
Perform a furnace tuneup
New heat and air system. Compressor broke. Best solution to save money on HVAC parts.