Give us a call! 405-912-5900
Interstate Heating and Air Conditioning has been the loyal provider of heating and ac repairs services in Edmond, OK since 2002. Our licensed ac technicians are in your neighborhood everyday providing exceptional customer service along with quality air conditioning repair and replacement. When something is wrong with your HVAC system look no further than Interstate Heating and Air. We can fix your ac and have you cool in no time.
If you want to see why Edmond, OK chooses us for heating and cooling when quality is needed, just have a look at our reviews.
The average range of air conditioning replacement costs in Edmond vary from $2,000 – $10,000. Why such a large range? It’s because there are so many variables that you can factor into your overall costs:
- Size of system
- Efficiency of system
- The condition of your air conditioning
- Any available financing plans
You can get a more specific answer about your air conditioning costs by calling an experienced air conditioning expert at Interstate: (405) 237-4937 or by filling out a quick form online.
Your HVAC system should be checked and tuned up if necessary by an HVAC company twice a year: once for heating and once for cooling.
Interstate is here to make sure that your maintenance brings you as many advantages as possible while reducing the stress of keeping up with it. Call (405) 237-4937 to discuss a plan that’s right for you.
There are so many variables that influence air conditioning repair costs that it’s practically impossible to name every one. But that main ones include:
- Where your unit has been maintained
- Extent of damage
- Part that needs repairing
If you would like a specific estimate for your AC repair, give Interstate a call at (405) 237-4937.
for Edmond, OK
Our Reviews by City
Steam humidifier install. Quick, efficient arrived on time.
DAVID - Edmond, OK
Humidifier works great, house much more comfortable.
Great technician — Professional and Kind
JAMES - Edmond, OK
Our technician was awesome/through! Great service from him.
Great Customer Service from outlet technician specifically.
Lara/Jim - Edmond, OK
TOM - Edmond, OK
Prompt response, and great followup
GARY - Edmond, OK
ROGER - Edmond, OK
Very conscientious, they are always quick to come out and service us
STEVEN MILLARD - Edmond, OK
Interstate always do a great job.
LYNN - Edmond, OK
Kianesh was very meticulous and thorough!
Great service. Awesome people.
HERSCHEL - Edmond, OK
LYNN - Edmond, OK
Kianoosh was very conscientious, very thorough, explained all that he would be doing, cleaned up after himself. I highly recommend him.
Meticulous quality of work
ROGER - Edmond, OK
Meticulous work, Jason and Jeremiah truly care about quality of their work
ROYDON - Edmond, OK
BETTY - Edmond, OK
My answer will always be the same, excellent service no matter who may come! All of your employees are, very courteous and knowledgeable!
Great service and easy to work with!
LYNN - Edmond, OK
BETTY - Edmond, OK
I have been with Interstate for seven years or more. I was referred by another veteran that I know! Never a complaint! These guys are top notch with me..
BETTY - Edmond, OK
I always get great service with Interstate H&A. whether to fix something or Do a routine check on the air conditioner or furnace. Thank you, ladies, for being so kind and helpful whenever I call🙋🏽♀️😉
LEWIS - Edmond, OK
On time, friendly and thorough!
Very pleased with the service
Wendy - Edmond, OK
The problem was quickly diagnosed and taken care of. Adam was very courteous and knowledgeable. I will most likely call again, if not even sign up for the maintenance service. Thanks!
CHARLENE - Edmond, OK
Adam found what was wrong right off. He also installed our unit 5 years ago. We sure would like to have him service our unit from now on if possible.
These guys are awesome!!
S Brown - Edmond, OK
been using them for two different houses we own and they are always prompt, courteuous and i can always trust their work. Would definitely recommend them!!
Brandon is great
JAMES - Edmond, OK
Good service, excellent person
MARCO - Edmond, OK
Technitian spreads a lot of trust. Very nice person too. I enjoyed his accent. Thanks for coming Brandon
Adam was very thorough and explained problem to us
ROGER - Edmond, OK
GARRY - Edmond, OK
Technician, Adam was very knowledgeable, friendly and service was great!
CHARLENE - Edmond, OK
Brandon was great, thanks.
I arrived to perform a silver member furnace tuneup. I checked all amp drawls voltages gas pressure igniters within specs re-surfaced flame sensor blower wheel is clean found no oil coming out of the blower wheel delta T is within spec customer previously changed filters. The system is in good operating condition as of today.
Part on order will return when parts arrive. This will be a warranty call only send myself to this call. Arrived with parts. Prior tech had low voltage running to high voltage components and low voltage running to high voltage components. All components in humidifier were destroyed. Due to amount of repairs needed to fix humidifier. I replaced whole humidifier. I wired in humidifier correctly. I used existing drain and supply line. I ran humidifier in all modes. Humidifier is working at this time. All above work performed under warranty. Charged for humidifier pad replacement
Performed silver club furnace maintenance. Customer recently replaced filters. Blower and evaporator are clean. Cleaned flame sensor and tested ignitor. Test induced draft motor. Test capacitor and motor amp draw. All capacitors and motor amp draw in range. Test gas pressure and temperature rise. Gas and temperature rise in range. Cycled unit multiple times to insure that all safeties are working and unit running as designed. System is heating as designed at this time. Ductwork in decent condition. Suggest adding surge protector to furnace in future to protect furnace electronics. Surge protector are 149.00 installed 3 yr warranty.
5yr manufacturer warranty
Arrived and found extremely out dated flue 6 inch and had leaked water before. Insurance suggested it be replaced discussed with customer the reason why it was out dated and where it did not meet code requirements and it it all should be replaced at a 4 inch diameter all the way down and a new cap customer gave approval went and got material and replaced entire flue total of 8 ft.
5 yr manufacturer warranty 1 yr labor. Water line and shut off replacement with filter.
I arrived at to perform to furnace tuneup for a red member. I checked all amp draws voltages resurfaced both flame sensors checked all capacitors both blower wheels are clean no leaks coming from either blower motor delta Ts are within spec change the filters in the garage unit at the outdoor unit did not need to be changed cycled both systems several times with all operations being normal. When I arrived the customer did have questions about a thermostat that was not working. I installed a new thermostat WiFi for her showed her how to use it And left all instructions with her. There is a three year labor warranty and a five-year part warranty on the thermostat. Informed the customer to give us a call if she is having any problems with the new thermostat.
I arrived at to perform a silver member fall and summer tuneup on both air conditioning and furnace. I checked all amp draws voltages all the capacitors for the compressor fan motor and blower motor resurfaceD the flame sensors both igniterâ€˜s are within spec all gas pressures are within spec as well both blower wheels are clean neither blower motor nor fan motors are leaking oil all delta Tâ€™s are within spec except for the Rheem unit on the air conditioning side due to low refrigerant charge I checked all the refrigerant charges washed all of the condensing coilâ€™s and cycled all system several times with all operations being normal except for the Rheem unit on the air conditioning side with the low refrigerant. The customer has been sent an estimate for 2 pounds of R-22 as well as a surge protector for the carrier furnace. Customer mentioned that they will look into putting more refrigerant in the unit next spring as well as installing the surge protector.
I arrived to a customer no heat on a newly installed furnace. During inspection I found that the GFI tripped. I cycled the system after the GFI was reset and checked the amp draws voltages. Thedraw for the inducer is .7 amps the amp draw for the blower motor is 1.3 A both of which are in spec could not find any reason the GFI would be tripping other than it is starting to intermittently fail or the homeowner is havingPower surges. System is operational as of today did inform the homeowner that if the GFI trips again and we come out without him replacing it there will be a service charge.
Blue shield fall service for 2018 Carrier 96% gas furnace. Filters were recently changed. Home has been cooling and heating well. Checked flue, condensate line and evaporator coil. Checked blower, blower capacitor and cleaned flame sensor. Took static pressure readings. Measured gas pressure and dialed down to 3.5â€ wc. Replaced gas caps. Measured heat rise, and inside delta t. System is operating well at this time! Spoke with customer about hot water tank and dryer vent maintenance. Also spoke about our IAQ products and sent a link to our videos describing them.
Blue shield plan fall service on 2007 Comfort Maker furnace. Changed filters included with plan. Talked about duct cleaning and the benefits of having ducts cleaned, customer said they would ask the homeowner about having it done. Cleaned flame sensor, checked flue. Checked evap coil, drain line and blower. Checked heat exchanger. Turned system in and checked heat rise, gas pressure and replaced caps after dialing down pressure. Checked electrical components and delta t. System is heating well at this time. Left an estimate for duct cleaning and dryer vent cleaning.
Blue shield fall service on 2015 Carrier Gas Furnace. Inspected flue, evap coil and drain line. Tested for carbon monoxide. Checked heat exchanger, blower and return plenums. Checked supply ductwork. Cleaned flame sensor and burners. Cycled system on and checked amp draws high and low, measured gas pressure heat rise and delta t. Left fresh filters included with blue shield plan with customer. System is ready to keep home warm this winter season.
Blue shield plan fall furnace tune up. Asked customer about how home is cooling and heating and how filters are doing. Customer needs to change filters, so left 2 fresh 14x30 filters included with blue spp. Home has been keeping temperature much better since replacing ductwork. Inspected ductwork, flue and cleaned flame sensor and burners. Checked evap coil, drain line and heat exchanger from below. Checked blower cabinet and blower capacitor. Capacitor is reading weak, 8.4/10 mfd. recommend having it changed. Checked heat exchanger from above. Cycled system on and tested gas pressure, replacing gas cap. Checked amps. Blower amps look good but inducer amps reading high at 2.0/1.7. Lubricated inducer motor and got amps down to 1.5 amps. Inducer still making a bearing running noise but reading in range. Measured heat rise and delta t. System is running at this time. Customer wants to wait for a future appointment to have blower capacitor changed.
Performed silver club furnace maintenance to both units. Changed filters. Blowers and evaporators are clean. Cleaned acid traps for 90 percent furnace flue drains. Cleaned flame sensor and tested ignitor. Test induced draft motor. Test ecm motor amp draw. All amp draw in range. Gas pressure and temperature rise in range. Cycled unit multiple times to insure that all safeties are working and unit running as designed. Both systems are running as designed at this time time. Both surge protectors are in working order.
Performed preventative maintenance on furnace for customer. Inspected filters, blower assembly, motor, electrical components, heat exchanger, burners, flame sensor, ignitor, gas valve, inducer motor, and overall condition of equipment. Checked thermostat operation, wiring, capacitor, amps, temperature rise and gas pressure. Flame sensor was cutting out intermittently. I recommended to customer to have the flame sensor replaced to fix problem now and eliminate having to replace it at a different time. Customer approved replacement. System has a high temperature split of 59-61 degrees. This is due to the return ducts undersized and not allowing the recommended amount of air flow back to the furnace to lower that temperature. Made homeowner aware of issues this could cause. We also discussed indoor air quality, and attic installation levels.
Came out to perform preventative maintenance on 2 Furnaces. House was built in 2008 and systems are original to the home. I changed the filters for customer throughout home. I inspected the blower assemblies, motors, electrical components, heat exchangers, burners, flame sensors, ignitors, gas valves, inducer motors and overall condition of equipment. Downstairs system had a weak ignitor. I discussed with customer about replacement before it fails. Customer approved repair. I replaced the ignitor. Checked amps, temperatures and pressures of both systems. Overall, both systems are holding up internally, there were no signs of cracks on heat exchangers visible at this time. Both furnaces are heating properly within manufactured specifications at this time. *As I was changing the filters, I noticed the returns had significant dust residue in them. I recommend customer have ducts cleaned soon to help clear out the dust in ductwork.*
Performed silver club heater maintenance. System is heat pump. Cycled emergency heat and tested amp draw. All elements in range. All sequencers and limits in working order. Capacitor and motor amp draw in range. Blower and evaporator are clean. Test capacitor and motor amp draw at condenser. Test compressor amp draw. All amp draw in range. Refrigerant levels are in range for current temperatures. Outdoor thermostat in working order. Ran unit in all modes of heating. System is heating as designed at this time. Surge protectors are in working order. Changed customer supplied filters.
Silver club fall tune up on 2012 Amana 80% gas furnace. Customer recently changed filters. Customer still having an issue with master bedroom keeping up, which is a Ductwork issue. Adding a return would help cycle the air in the master suite better, which is on the far end of the home. Checked flue, coil and drain line. Checked ductwork, blower and blower capacitor. Checked and cleaned flame sensor and burners. Checked heat exchanger from both sides. Cycled system on and checked gas pressure, replaced gas caps and checked amps. Measured heat rise and inside delta t. System is in good condition to warm home this winter.
Blue Club Fall PM. Upstairs system. Checked filters and changed 14x30 and 14x24 filters in downstairs system. Inspected evap coil, drain line, flue and ductwork. Cleaned flame sensor and burners. Checked blower , blower capacitor and heat exchanger. Cycled system on and checked gas pressure, replacing gas cap. Checked amps inside delta t and heat rise. System is operating well at this time. Talked about our duct cleaning and dryer vent cleaning services.
Silver Club Fall PM. Downstairs system. Checked filters and changed 14x30, 14x14, and 12x24 filters in downstairs system. Inspected evap coil, drain line, flue and ductwork. Cleaned flame sensor and burners. Checked blower , blower capacitor and heat exchanger. Cycled system on and checked gas pressure, replacing gas cap. Checked amps inside delta t and heat rise. System is operating well at this time. Talked about our duct cleaning and dryer vent cleaning services.
Performed silver club furnace maintenance to system. Changed filters per customer. Cleaned flame sensor and tested ignitor. Test induced draft motor. Capacitor and motor amp draw in range. Gas pressure and temperature rise in range. Ignitor in range. Cycled unit multiple times to insure that all safeties are working and unit running as designed. System is getting older and showing signs of age but working at this time. Customer will see what happens with system before making any repair or replacement decisions.
I arrived to perform for a silver membership. For the upstairs furnace I checked all amp draws voltages gas pressure igniters within spec resurfaced flame sensor blower wheel is clean checked capacitor and delta T cycled the system several times. During this inspection I did find that the blower capacitor is out of range it is 11 ÂµF out of 12.5 and should be replaced. Other than that no issues were found. I checked all amp drawls voltages gas pressures resurface flame sensor igniter is within manufacture specs blower wheel is clean capacitor is within delta T is within spec as well. The draft inducer assembly is over amping slightly 2.9 out of 2.8 and making Whining noise. The customer has declined all repairs as of today and would like a estimate sent. Customer also declined having all of his filters changed by us.
Arrived to service call and performed system evaluation. Found bad blower motor. Tried to install motor it would not fit. Will have to get Oem motor and return. I arrived to a previously diagnosed blower motor that was failed. I installed new OEM blower motor reassembled the furnace and cycled the system several times with all operations being normal. One year parts and labor warranty.
I arrived to perform a silver member furnace tuneup. I checked all amp draws voltages gas pressure resurfaced igniter cleaned spark rods checked capacitor blower wheel is clean delta T is within specs. Cycled system several times with all operations being normal. Customer did mention that his thermostat goes blank at times it is a power robbing thermostat but I put batteries in it to see if that will eliminate the issue. Informed the customer that if it does not illuminate the issue to give us a call and we should be able to do a part warranty.
I arrived to perform a fall service on a blue membership. I checked all amp draws voltages gas pressure resurfaced flame sensor and cleaned the spark rods checked capacitor blower wheel is clean delta Tâ€™s are within spec cleaned both washable filters. During the inspection I did find the capacitor for the blower was out of spec 13.5 out of 15 ÂµF. Customer has authorized the replacement of the capacitor. I replaced the capacitor and cycled the system with all operations being normal as of today one year par and labor warranty.