Give us a call! 405-912-5900
Interstate Heating and Air Conditioning has been the loyal provider of heating and ac repairs services in Edmond, OK since 2002. Our licensed ac technicians are in your neighborhood everyday providing exceptional customer service along with quality air conditioning repair and replacement. When something is wrong with your HVAC system look no further than Interstate Heating and Air. We can fix your ac and have you cool in no time.
If you want to see why Edmond, OK chooses us for heating and cooling when quality is needed, just have a look at our reviews.
The average range of air conditioning replacement costs in Edmond vary from $2,000 – $10,000. Why such a large range? It’s because there are so many variables that you can factor into your overall costs:
- Size of system
- Efficiency of system
- The condition of your air conditioning
- Any available financing plans
You can get a more specific answer about your air conditioning costs by calling an experienced air conditioning expert at Interstate: (405) 237-4937 or by filling out a quick form online.
Your HVAC system should be checked and tuned up if necessary by an HVAC company twice a year: once for heating and once for cooling.
Interstate is here to make sure that your maintenance brings you as many advantages as possible while reducing the stress of keeping up with it. Call (405) 237-4937 to discuss a plan that’s right for you.
There are so many variables that influence air conditioning repair costs that it’s practically impossible to name every one. But that main ones include:
- Where your unit has been maintained
- Extent of damage
- Part that needs repairing
If you would like a specific estimate for your AC repair, give Interstate a call at (405) 237-4937.
HVAC maintenance should cost around $150-$350 per year in Edmond, OK. HVAC maintenance typically includes:
- A cleaning of your HVAC unit.
- An inspection of your HVAC unit.
- A lubrication of your HVAC unit’s moving parts.
- A replacement of your HVAC unit’s air filter.
If you get your HVAC system on a maintenance plan, you will usually be able to receive additional benefits such as discounts on service calls and repairs. To get your HVAC system maintenanced, call us today.
You should schedule a tune-up for your AC system twice a year (once in the Spring and once in the Fall). AC maintenance typically involves inspection and testing of the system to make sure it’s working as efficiently as possible, including cleaning, lubricating, tightening and calibrating the AC components. Seasonal service appointments are essential in making sure your AC lasts a long time and functions at maximum efficiency.
Interstate Heating & Air Conditioning can help make sure that your system continues to supply you with cool air for many years to come. For more information on the AC services we offer, call us today.
Yes, having your AC routinely serviced is vital in making sure your unit continues to run as efficiently as possible and doesn’t run into any problems. It can also help to extend the life of your system, improve your air quality and save you money on your energy bills. You should aim to have your AC serviced at least once a year.
To find out how Interstate Heating & Air Conditioning can help you improve your AC system, call us today.
If your AC isn’t cooling, it could be a sign that a number of things have gone wrong with your system. Some of the most common causes of this include:
- Dirty air filter.
- Thermostat set to “on” instead of “auto.”
- Refrigerant leak.
- Blocked condenser unit.
- Damaged compressor.
To find out how Interstate Heating & Air Conditioning can help you improve your AC system with maintenance or repair, contact us today.
for Edmond, OK
Our Reviews by City
RUSSELL - Edmond, OK
Maintenance, Service & Communication
LEWIS - Edmond, OK
Chris took good care of my equipment, focusing on a couple things of items that might be a problem down the road. Meets my expectations…every time!
JOHN - Edmond, OK
Chris checked our unit, cleaned our air conditioner, and changed our filters.
GARY - Edmond, OK
JEFF - Edmond, OK
Excellent job as usual
GEORGE - Edmond, OK
Great service by Chris
JONATHAN - Edmond, OK
Punctual, professional and fixed the issue.
HERSCHEL - Edmond, OK
Everyone at Interstate has been courteous and professional. Chris is no exception. He was meticulous in doing his job and I have complete confidence in his work and in Interstate Heating and Air. Highly recommend them to anyone.
APRIL - Edmond, OK
efficient service by tech Isaac
KEN - Edmond, OK
Very knowledgeable and helpful
BRENT - Edmond, OK
I appreciate Jake’s time to explain everything. He came ready to work.
Thorough, knowledgeable, and kind
SHERI - Edmond, OK
I’ve always been happy with the service and products from this company, but I have to give special thanks to Jason who came to do my semi-annual check and was not only professional and thorough, but offered to help with anything else I might need afterward. Not just a good company, but genuinely good people.
KEN - Edmond, OK
KEN - Edmond, OK
representative very efficient
Isaac is the best
EMILY - Edmond, OK
Isaac is our favorite technician. He is so kind and understanding. He takes great care of us.
EMILY - Edmond, OK
BRETT - Edmond, OK
Summer annual tuneup
DAVID - Edmond, OK
Great, efficient service
CHERYL - Edmond, OK
I’ve been impressed with Interstate Heat and Air. This was their second visit to my home. Both times they were here early and worked very hard to make sure both my A/C and heater were functioning properly.
Great Service, Thorough, Fair Price
Lara - Edmond, OK
Eilane - Edmond, OK
Always a pleasure to do business with interstate heating and air. Great customer satisfaction always.
A/C Check up & Dryer Vent Cleaning
STEVEN MILLARD - Edmond, OK
Absolutely GREAT! Your employee is very good and very informative when I had questions.
Outstanding as always
GARY - Edmond, OK
Chris did a great job explaining everything to me.
JOHN - Edmond, OK
Fantastic service. He not only took care of our air conditioner he helped to prepare and serve our dinner. Truly a man of God.
KATHY - Edmond, OK
Arrived on 15 October to conduct fall tuneups times three Blue Shield member.Started with the upstairs furnace had to adjust the gas pressure it was 5 inches water column and brought it down to 3.452 inches of water column removed cleaned and replaced flame sensor after cleaning it was at 4 DC millivolts. On the upstairs had to hand start the inducer motor it was locked up recommend replace the inducer motor. Also inspected heat exchanger on the upstairs and tested hot surface igniter checked all electrical circuits on system everything else on the system is within manufacture specifications as well as heat rise.Living room furnace gas pressure first fired up was over 4 inches of water column reduced it down to 3.504 inches of water column cleaned and reinstalled is currently running at 3.9 BC millivolts Tested hot surface igniter inspected heat exchanger temperature rose is at 36Â° manufacture specifications 30 to 60Â° living room furnace is running at manufacture specifications. Mast
Arrived on 15 October for a fall tuneup silver club change filters in customers unit removed cleaned and reinstalled flame sensor ohmed Hot surface igniter tested gas pressure took a temperature rise in at 42Â° temperature rise and manufacture specifications states between 40 and 70. Heat exchanger was inspected tested induced raft motor specked it flue. Everythingâ€˜s within manufacture specifications.
Arrived on 15 October for a full tuneup blue club change filters in the house upon section of the unit noticed that the union had a small gas leak was able to take the union apart clean the meeting surface reinstalled retested with soap bubbles no leak was present. Inform the customer of a previous condition of the unit was a collector box threads were damaged upon install it is not leaking at this time but wanted to reiterate the potential failure points. Cannot check gas pressure on gas valve due to stripped service port informed customer of this checked heat rise flame sensor all electrical components it is currently running at manufacture specifications at this time. Customers complaint was last winter that his 90% furnace froze up due to cold conditions previously gave customer estimate to install heat tape customer does not want to do it at this time. Thank you for your business Chris.
I inspected a 2 ton air handler and heat pump for replacement. The owners will be responsible for contacting the neighbors about removing their fence and gaining access to get the units into and out of the back yard. The system will not be up to code if we install it in the same location with the same electrical set up. We will have to move the disconnect and add a condenser pad and pump ups to bring the system up to code. We will be following up with the customer Friday after 2 Pm.
Arrived on site for fall tuneups times for inspected blowerâ€˜s here exchangers flame sensors hot surface igniterâ€™s gas pressure readings temperature rises expected limits pressure switches Indus motors Flues all these units are 90% furnaces check drains to ensure proper flow.
I arrived for a blue club member on a system that is having a noise issue and a water problem. I inspected the system and found the duct to not be insulated and sweating and dripping onto the dip ceiling. I also found the system to be stopped up in much the same condition as it was when we first cleaned the system. The blower wheel is getting stopped up with dust and heavy debris causing the wheel to become unbalanced and cause the system to vibrate. I recommend to clean the evaporator coil and blower wheel at this time. They are going to try and change their product and have us clean the system after their product change. Then we will proceed with the systems normal maintenance to keep the systems running properly.
Came out to a call for an AC not cooling properly. I checked system over and found it completely frozen over all the way out to the AC unit. It has 2-3â€ of Ice on the compressor. Told customer I wouldnâ€™t be able to do anything about the unit today due to how much ice it has on it. The evaporator coil is a solid block of ice and the heater would trip on high limit due to lack of air flow. No one is in the home this weekend, so we scheduled to come back out Monday.Arrived on October 11 for a follow up on frozen system conducted minor leak search only found the net going to be fixed orifice where is the small leak on it and this was a combination of extremely dirty air filter in a small leak customer topped off after we check no leaks system is working as it should after adding 1 pound of 410 A
Arrived on 11 August for fall tuneups times three inspected all evaporators he exchangers induced draft motor flame sensors hot surface igniterâ€˜s tested humidifiers both humidifiers are not working at this time customers think about replacing them.Induced draft motor on the southside has a bearing going out gave customer an estimate for replacement but also just thinking about replacing that system tested gas pressure temperature rise customer changes on filters the upstairs unit flu does not have enough clearance around it customers gonna get a roofer to fix the issue the drain for the main system that goes into the slab is overflowing customers going to get a plumber to fix that issue. Thank you for your business Chris.
On October 9, 2021 I arrive to a silver club member for a full tuneup upon arrival I greeted the customer I then went to the furnace in the attic I did amp drawls on the blower motor and the inducer motor and then pulled and cleaned the flame sensor then amp draw on the hot surface igniter and check the gas pressure everythingâ€™s working properly at this time thank you for your business Mike t
Arrived on 7 October for a full tuneup inspected blower hot surface igniter flame sensor induce draft motor flu pipe change filters in the house customer provided took temperature rise and gas pressure was within manufacture specifications.
Dryer vent cleaning attic discharge, inspected dryer vent in attic and it is making a fairly straight run, ran spinning brush from below with 5 passes and shop vacced out about 5 gallons of dryer lint. Cleaned dryer exhaust in unit by hand up to the impeller, cleaned surrounding area and back of dryer with shop vac. Verified dryer exhaust is clear with inspection camera. Set everything back in place and verified proper dryer function.
Arrived on 7 October for two full tuneupâ€™s Blue Shield checked hot surface igniterâ€˜s on both units flame sensors blowers induce motors check heat rise on both units I was within manufacture specifications change filters customer provided filters does not like our filters also checked gas pressures on both units.
Duct cleaning estimate for blue shield plan member. 12 supplies and 1 return. 2 ducts over smaller bedrooms are loose, so I connected them properly with screws and sealed with metal tape as a courtesy. Layed drop sheets where needed. Cleaned vents and grills. Duct cleaned all ducts with 1-3 passes each. Sprayed in hospital grade disinfectant and replaced vents, customer supplied filters and grills. Cleaned up excess debris, and set thermostat back to customer preferred settings.
Arrived on 6 October for a furnace tuneup removed cleaned and replaced flame sensor on down hot surface igniter inspected flu check drain line for 90% furnace customer change their own filters inspected blower tested both capacitors for inducer motor and blower motor check gas pressure took a reading for a temperature rise 50Â° and manufacture specifications is between 50 and 80.
Ring the doorbell twice customer did not answer the door call tried to call the customer customer did not answer the phone we will put the job on hold to try to reschedule with a customer I arrived for a new customer tune up on we failed to keep good communication with throughout the experience with Interstate. I first spoke with the homeowner about what they were expecting from Interstate and what I had to offer to benefit them and what they were needing. I spoke with the homeowner and offered for them to come with me to inspect the system and see how the system is running first hand. We found a 4 ton system on a 2600 sq foot home with 4 ton supply dust and 2.5 ton return duct. I also found the evaporator coil leaking refrigerant and oil on a R22 system. We discussed all options on repairing the system and on replacing the system. We decided to leave the furnace in place and bud a 4 ton evaporator coil and a single speed condenser and a two speed condenser. I made them aware of the
05OCT2021 Jason B Arrived for for fall tune up. Spoke with Audrey about systems performance. Started at the furnace. pulled and cleaned the flame sensor. checked the blower, heat exchanger, capacitors, HSI, burners, evaporator coil, and all safeties cycled system on and checked inducer, gas pressure, temperature split, and CO Levels. Scrolled through all four zones at the thermostat and verified proper operation. Inspected AC system and found surge protector out. This system is running properly at this time. Attached is a quote for the Surge protection replacement.
Arrived on 5 October for a thermostat problem it is a nest thermostat it was cycle on the air conditioner for probably five seconds and cycle off went into the attic to verify problem wasnâ€™t on the furnace removed all thermostats wires off of the control board jump without control board to allow air conditioner to run when that happened it started overheating the transformer and AC still did not run problem is in the control board and transformer gave customer estimate for universal control board and transformer might want to replace system. Chris
05OCT2021 Jason B Arrived for for fall tune up. Spoke with Sarah about systems performance. This furnaces have not been run this season. Cycled systems and humidifiers on at the thermostat. pulled and cleaned the flame sensors. checked the blower, heat exchanger, capacitor, HSI, burners, evaporator coil, and all safeties. cycled systems on and checked inducer, gas pressure, temperature split, and CO Levels. Systems are running properly at this time. Replaced filters and customer supplied humidifier pads. West side furnace found ground wire frayed and Romex connect not properly terminated. Disconnected power and re-stripped ground wire. Reconnected romex connect. On the east system there was a concerning about of calcium build up inside of the humidifier. Brushed out excess build up and flushed drain line with water. Systems are running properly at this time, I will be following up with Sarah about replacing the water softeners leading to fan powered humidifiers. Current indoor humi
Arrived on 2 October for an air conditioning knuckle found that the hard start kit and the capacitor were both blown customer authorized replacement with a turbo 200 X and a new hard start kit installed parts check charge on unit it had 20Â° of superheat with 4.5Â° of sub cooling compressor had 16.9 A while the condenser fan motor had 1.3 A.
Arrived on 1 October for two air conditioning preventative maintenance service and two full services silver plants customer change their own filters inspected blowerâ€˜s evaporator drain lines here exchangers inspected contactors capacitors tested all contactors and capacitors everything was within manufacture specifications checked charge on both units checked temperature rise on both units upstairs furnace was at 33Â° temperature rise manufacture specifications for both units is 30 to 60 downstairs furnace temperature rise was 30Â° everythingâ€™s within manufacture specifications on these units.
Arrived on 30 September for two full tuneupâ€˜s expected blower hot surface igniter flame sensor take a temperature rise reading it was at 62Â° manufacture specifications is between 45 and 65.Inspected flu change filters customer provided did not want to use filters included in service specked it induce motor here exchange. Tested heat pump mini split in a 33 temperature split system is working well at this time.
Jake, Chris. We arrived to balance a home out that we recently replaced the system and the duct work. We checked the air flow in every room and grill and documented our findings. We then lowered the air flow in the rooms that were getting most of the air flow. We then rechecked all rooms and found that we improved the air flow in the rooms the homeowner wanted to stay cooler. We cleaned all grills and vacuumed all debris in the home. If you have any questions please contact us and we will be happy to help you in anyway possible.
Arrived on the 28 September for a fall tuneup inspected the evaporator and blower tested electric heat each element had 20 amps tested heat pump and defrost cycle changed filters customer provided everything s within manufacture specifications.
Arrived on 27 September for a furnace tuneup Blue Shield expected evaporator blower zoomed out hot surface igniter and 51 homes on it remove cleaned and replaced flame sensor while testing flame sensor had 3.9 DC Milla amps on it motor had .8 A the temperature rise was high due to not enough return but there is not enough room in the closet to add extra return for the unit made customer aware of the situation checked for from carbon monoxide none was found checked gas pressure on gas valve it was running at 3.2 inches of water column change filter and customers house.
Arrived on 27 September for three air condition preventative maintenance is inspected all the blowers evaporatorâ€™s drain lines contactors capacitors everything checked out checked refrigerant everythingâ€™s within manufacture specifications changed all the filters in the house.