Give us a call! 405-912-5900
Interstate Heating and Air Conditioning has been the loyal provider of HVAC services in Oklahoma City, OK since 2002. When your AC or furnace is not working, our pros can get your heating and cooling running again. We are experts when it comes to HVAC repair, Air conditioning replacement and all types of furnace services.
If you want to see why Oklahoma City, OK chooses us for heating and cooling when quality is needed, just have a look at our reviews.
With a heating and air conditioning tune-up in OKC–and with the right HVAC company you can expect:
- Greater energy efficiency
- Fewer breakdowns
- Less costly repairs
All of this adds up to more money savings. Plus, you can expect higher quality heating and cooling. To take advantage of these benefits, call Interstate at (405) 237-4937.
Typically, if your heating and air system is making loud noise, something is wrong with it. If you are hearing hissing, banging, squealing, buzzing, clicking or any other obvious noise, you should call a trusted HVAC company for service. Interstate is available for convenient scheduling at (405) 237-4937.
The decision to repair or replace your AC system is dependent on:
- Age – Is it over 15 years?
- Energy costs – Are your energy bills slowly climbing?
- Your comfort level – Are you still comfortable in your home?
- Home additions – Have you added to your home?
- And more
Get professional guidance on whether you need a replacement or repair by calling the HVAC pros at Interstate: (405) 237-4937.
AC tune-ups make sure your air conditioner is running optimally and can also help to extend the life of your unit. The cost to have your AC professionally serviced usually falls between $75-$200. You should have an AC tune-up scheduled once a year in the Spring to make sure it lasts you throughout the hot Summer.
You can count on the experts at Interstate Heating & Air Conditioning to deliver quick, expert AC tune-up services. Contact us for more information today!
There are a few ways you can tell if your thermostat has gone bad, including:
- Your thermostat won’t turn on.
- Your HVAC systems keep turning off and back on again.
- Uneven temperatures from room to room.
- Your thermostat is over 10 years old.
Interstate Heating & Air Conditioning can answer questions you have about your AC thermostat. Call us today and we’ll be happy to help!
There are a few reasons why your AC may not be turning on. Some of these include:
- Dirty Air Filter
- Tripped Circuit Breaker
- Refrigerant Leak
- Blown Fuse
- Dirty Coils
No matter what the condition of your AC is, Interstate Heating & Air Conditioning can figure out what the problem is and fix it quickly. Call us today for expert AC repair services!
for Oklahoma City, OK
Our Reviews by City
LORRI - Oklahoma City, OK
Jake was very perfessional. He had a lot of patience and was not pushy
Good Tune Up
BARRY - Oklahoma City, OK
Even though Jason gave me bad news, i felt like Jason did a thorough job . excellent service!
Good work and cut me some slack on the cost.
WALTER - Oklahoma City, OK
I’ll be calling Interstate in the future.
SABRINA - Oklahoma City, OK
Scheduling was a snap and quick. The technician was on time, listened to all my concerns, explained options, executed my selection and clearly explained what was being done, how the system works and what the expectations were as a result of the work done. I could not be happier. Best customer service I've seen from any company in quite some time!!
Informative and friendly!
ZACHARY - Oklahoma City, OK
Got me what I wanted, was courteous and quick, and informative
RONALD - Oklahoma City, OK
Good job, thank you Jake
CATHY - Oklahoma City, OK
Timely Efficient service
SUSAN - Oklahoma City, OK
Called late one night when A/C quit working on a hot day and they were able to come out the next afternoon. They discovered the problem and had the motor on hand that was needed so they were able to fix it on the spot.
Service was good
DANA - Oklahoma City, OK
FOXCROFT - Oklahoma City, OK
EDWARD - Oklahoma City, OK
Efficient and timely service
robert - Oklahoma City, OK
JAMES - Oklahoma City, OK
NATHAN - Oklahoma City, OK
Very good service
Steve - Oklahoma City, OK
Professional and knowledgeable
Chris did a great job.
CHARLES - Oklahoma City, OK
CHRIS WAS VERY NICE
Laura - Oklahoma City, OK
I was very happy when Chris came out and told me I didn't have a major problem. I am so afraid of people taking advantage of an older woman that's widowed but he was great found the problem fast. Thank you Chris I appreciate you.
AIMEE - Oklahoma City, OK
Great Service..Awesome price!!
Jd - Oklahoma City, OK
Great Customer service!
MIKE - Oklahoma City, OK
Always good service, pricey though
CHAD - Oklahoma City, OK
Isaac does great work but the cost is expensive
LAZETTE - Oklahoma City, OK
Great experience as always.
Great service! Mike did a great job!
Kelly - Oklahoma City, OK
TERMINIX - Oklahoma City, OK
Polite, professional and courteous.
KEELEY - Oklahoma City, OK
Mike was respectful, answered all my questions, and was early! Will be referring interstate to friends and family. Especially appreciated him covering his shoes before he came inside.
On July 25, 2021 I arrive to a previous customer nonmember upon arrival I agree to the customer they stated that the outdoor unit was making a loud noise and it wasnâ€™t cooling went to the outdoor unit and checked to see what it was doing the fan would only spin off if it was forced to spin manually opened up the service panel check the capacitor it was actually popped informed the customer that said put a new one in install a new capacitor checked amp drawâ€˜s condenser fan motor was pulling 1.1 A check the charge unit had 16Â° superheat the house is 90Â° inside everything is working properly at this time thank you for your business Mike T
On July 25, 2021 arrive to a previous customer nonmember upon arrival I greeted the customer they stated that the unit wasnâ€™t cooling properly I went to the condenser as the customer was kicking the thermostat on I checked the condenser it was extremely dirty and I disassembled washed it reassembled and check the charge the charger spot on it has 12Â° superheat After I washed it the head pressure was high tested system operations everythingâ€™s working properly at this time thank you for your business Mike T
On July 24, 2021 arrive to a new customer nonmember upon arrival I greeted the customer and they stated that the condensing unit was making a loud humming sound occasionally and there it was not cooling I went to the condensing unit pull the disconnect hooked up my amp clamp and the universe pulling 127 A to 135 A which is lock rotor I called the customer over and showed her what it was doing and explain to her that the compressor is locked upCausing the house not to cool she wanted a quote for compressor replacement as well as total system replacement
On July 24, 2021 arrive to previous customer for a water leak upon arrival I greeted the manager at the store and then climbed up on the roof check the drain he did have another back up been in the water push the clog down to the drain spout Iâ€™ll get in there and make sure I get everything cleaned out and vacuumed out the area where the compressor sits everythingâ€˜s working properly I got everything cleaned out and the drain is flowing like it should no other issues thank you for your business Mike
I arrived to inspect a air conditioner and see what it would take to repair the system or replace the system. I called and left messages for the owner but did not set ahold of anyone. I inspected the 19 year old R22 gas package unit and the duct work under the home and I recommend to repair the system only going off of age and condition of the system in a not running state. There is no power to the house at this time. I cannot check the system properly with no power at this time.
I arrived for a non member no heat call I inspected the system and found the gas valve shut off valve to have broken off the furnace. I so with the homeowner and they only wanted to do what repairs that the system needs to cool. I inspected the air conditioner and furnace and found multiple major issues with the furnace and air conditioning system. The issue with the outdoor unit are - capacitor leaking oil and non readable - contactor is chattering and blackened and pitted - the condenser fan motor is running at 1.18 amps / 1.00 amps - the compressor is running at 18.6 amps /17.4 amps - the systems superheat is running at 0.0 deg out of 11.5 deg superheat - the head pressure is exceeding 400 psi on a R22 system. The indoor issues are - evaporator coil is not accessible (probably dirty due to poor filtration) - no proper filters set up - gas valve is non operational- heat exchanger is extremely rusted. I made all issues aware tot the homeowner and we decided to bid to replace all compr
23JUL2021 Jason B Arrived for two system spring tune up, and spoke with Homeowner about the systems performance. Cycled both systems on at thermostat. Inspected coil, blower cabinet, motor and all electrical components at the furnaces. Inspected pressures, capacitors, fans, and compressors. Washed out condenser coils. Cycled systems back on. Filters were recently changed so I left existing filters in and new filters in indoor furnace closet.
I arrived for a new customer new system bid replacement. I spoke with the homeowner we compared bids and looked over financial options and payment plans. We were approved for financing for 10% for 138 months and the homeowner approved and accepted the terms and activated the loan. They then changed their minds and wanted to see if they can change the loan to 0% for 24 months. I contacted GreenSky and it will take 24 business hours to change the plan number and see if itâ€™s approved if GreenSky approves the application by Saturday for 0% for 24 months we can install the system on Tuesday. If we canâ€™t get financed completed by Monday we will have to move the installation day to Friday. I made the homeowner as of this issue. They are also aware of not getting 10% off the system installation with financing. If they pay the system off in full there is a 10% discount off the system equipment. We decided to purchase a 10 year labor warranty with a blue club maintenance plan along with the
Silver club summer AC service, checked thermostat, washed condenser thoroughly, washing between both coils. Checked dual capacitor, tightened wire fittings, and cleaned contactor connect points from dust buildup. Checked evap coil, drain and filter. Checked blower. Cycled system on and checked electrical, delta t and refrigerant pressure. System is working well at this time!
23JUL2021 Arrived for spring tune up, and spoke with Jeff about the systems performance. Cycled system on at thermostat. Inspected coil, blower cabinet, motor and all electrical components at the furnace. Inspected pressures, capacitors, fan, and compressor. Washed out condenser coils. Cycled system back on. This system is running like a dream at this time! Jeff it was good meeting you, I hope that hot tank goes smoothly! Capacitor is getting low, but still within specs.
Blue shield summer service. Replaced filters (3). Blower motor is ECM no cap required. Blower motor and wheel are clean, condensate drain line is clear. Washed condenser coil, compressor capacitor is good, condenser fan motor is ECM, no cap required, contactor is good. Checked operation, all amps and pressures are good. System operating normally.
I arrived for a silver member ac pm. I spoke with the homeowner and found that the system is running and shutting off normally. I inspected the indoor system and found the filter in need of replacement. I replaced the filter for the homeowner. We do not need to order more filters at this time. I inspected the indoor system and found all components to be running properly at this time. I also inspected the outdoor condenser and found the coil to be dirty. I cleaned the condenser coil and checked the systems operation and found no issues with the outs unit at this time. Overall this system is running properly at this time.
Came out to call for a system not cooling properly. Customer stated that the system stopped cooling last night completely and hasnâ€™t kicked back on since. I checked system over and found the capacitor was bad and not allowing the system turn on. Customer stated that they havenâ€™t had any maintenance done on the system, but they do change the filters regularly. Recommended repair and maintenance plan. Customer approved both. I made repair and washed the condenser coil thoroughly. This call does not count as their first service. The first service will be done in November. I made sure system was operating properly within manufactured specifications. Customer had a problem room and asked for recommendations to fix the air flow in the room. I gave him a quote for air balancing and adding a return to the room as well.
On July 22, 2021 arrive to a previous customer nonmember upon arrival I Greeted the people renting the matzo device they stay there wasnâ€™t cooling checked everything out check the charge did amp drawls went through the entire unit and tested everything everythingâ€™s working like it should itâ€™s cycling on and off and running like it supposed to and I watched it run to make sure everythingâ€™s doing what it supposed to be doing
I arrived for a blue member ac pm. I spoke with the homeowner and and found the system to be running with no issues. I inspected the condenser and found it to have a good layer of cotton wood on the condenser. I clean the condenser and checked all amps refrigerant charge and electrical components and for no issues. I also checked the furnace and evaporator coil in the attic and found no issues with the system in the attic.
I arrived for a silent member ac pm. I inspected the system and found the outdoor system to be extremely dirty and muddy. I also found the filter to be the same filter I installed on last service. I recommended to install a 4â€ agin to help prevent the blower motor from getting dirtier than it already is. The homeowner wanted to only put in a 1â€ filter in at this time. I replaced the filter and clean the condenser coils. I made the homeowner aware that this system is getting older and itâ€™s getting to be in bad shape due to the outdoor system is in the same area as the pig and the filter is not being replaced when needed. I strongly recommend to replace the filter at least once a month if they continues to use a 1â€ filter.
I arrived for a silver member ac pm. I inspected the indoor and outdoor system and found that the condenser coil was completely stop up and the condenser fan motor is running hot and leaking oil out of the bottom bearing. I cleaned the condenser coil and checked the systems operation and found the motor to be running at 0.78 amps out of 1.10 amps per manufacture specifications. I explained this to the homeowner and I recommended to replace the conditioner fan motor to prevent a breakdown. We decided to not replace the motor at this time. I have them a additional discount to replace the motor at this time. I also gave them 30 days for the same price to replace the condenser fan motor.
Came out to call. Customer stated that the system wasnâ€™t cooling and it didnâ€™t seem like the compressor was on. I checked system over and found the system completely out of refrigerant. Customer had his roof redone recently, so I did a complimentary leak search to test the lines. Pressurized the lines with nitrogen and found a leak in the lineset. Location of leak is hard to get to, so I recommended replacement of the copper lines. Due to age of equipment and type of refrigerant, I recommended replacement also though. Customer wanted an estimate for replacement.
I arrived for a blue member ac pm. I spoke with the homeowner and found that the system runs normally and there are no issues that they know of. I inspected the indoor and outdoor system and found the system to be running properly at this time. I checked all amps indoor and outdoor temperatures and pressures and found no issues with the systems operation at this time. I noticed that the thermostat is getting hard to press the buttons on the thermostat to change the temperature. I suggested to replace the thermostat to a better thermostat so changing the systems set points are easily done without hassle. We agreed to replace the thermostat. I installed the thermostat and showed the homeowner the option of the thermostat.
On July 21, 2021 I arrive to a new customer nonmember upon arrival I agree to the customer they stated that the outdoor unit was not doing anything had a customer kick the unit on the fan did not spin compressor did not turn on opened up the service panel found the capacitor had popped call the landlord and let him know what was going on and pricing information customer approved of it over the phone get the new part installed start the system up everything photo did amp draws check to charge unit head 11Â° sub coolingEverything is working properly at this time thank you for your business Mike T
I arrived to replace a smoke detector on the HR room and inspect the upstairs conference room. I inspected the indoor system and found the air handler to be working properly at this time. I then inspected the outdoor condenser and found the compressor to be running extremely loud with a clanking sound while running with a high amp load and extremely hot to the touch. I turned the compressor off and cooled the compressor off with water and cleaned the condenser coils. Once the complete was cool to the touch I cycled the compressor on and the company started running at 23 amps and the compressor is not to pull more than 14.4 amps while itâ€™s running. As I was checked the system refrigerant charge the compressor stopped making noises and it dropped its amp draw down to 9.4 amps. I check the systems refrigerant charge and found all other components to be running properly at this time. I made this aware to Randy and we are leaving the system running for now. I strongly recommend to replace
21JUL2021 Jason B Arrived for spring tune up, and spoke with Barry about the systems performance. Cycled system on at thermostat. Inspected coil, blower cabinet, motor and all electrical components at the furnace. Inspected pressures, capacitors, fan, and compressor. Washed out condenser coils. Cycled system back on. Changed customer supplied filter. Found the compressor over amping at 20.5a / 17.5 the contactor at 0/40 and 6.9/7.5 with the age and condition of the condenser we decided to run it to the grave. The system is performing to the best of its abilities.
I arrived for a blue member no cool call. I inspected the HR department system and found the smoke detector to have lost power through the system preventing the system from coming on. We need to pick up the parts to replace the smoke detector.
Came out to call for a system not cooling properly. Customer stated that the AC wasnâ€™t cooling like it normally does and said the outside unit wasnâ€™t running either. I checked system over and found a bad fuse, replaced fuses with customer approval. Cycled system on and found the condenser low on refrigerant. Customer has had another company out the past two years to check the system and itâ€™s been low on refrigerant. The system is only 6 years old. I recommended doing a leak search and seeing if we can find the problem and fix it, or replace if needed. Customer wanted to have a leak search done. Told her I would get it scheduled, and we will be back out to do it. Came out to perform a leak search on the system. Used my leak detector and checked all major welds, evaporator coil, and outside condenser. Leak detector went off by the service port, but I checked it with bubbles and didnâ€™t have a hit. Customer has had another company out multiple times, and they couldnâ€™t find one e
On July 21, 2021 arrow to blue club member for spring tuneup upon arrival I greeted the customer and then went to the thermostat turn the system on and check thermostat operations I then went to the furnace did amp drawâ€˜s checked blower checked evaporator coal and changed filters I then went to the condenser your damn drawers check the components washed the condenser and tested system operations everythingâ€˜s working properly at this time thank you for your business Mike T