Give us a call! 405-912-5900
The road to comfort in Midwest City, OK is Interstate Heating & Air Conditioning. We offer the best service for AC repair and furnace repair. See all of our 5 star reviews as proof. Interstate heating & air is committed to our customers and to being there when you need us. From Air Conditioner Maintenance to AC and furnace replacements, you can count on Interstate Heating and Air.
Call us for services like:
Read our Midwest City, OK reviews to see why we are the trusted route for reliable heating and air conditioning services.
A new furnace or AC system in Midwest City should cost anywhere from $2000 – $10,000. It’s a wide range, and there are many factors that are going to influence your specific cost, including:
- Available financing
- The state of your air ducts
If you want to know your specific pricing options, give your local Midwest City HVAC experts a call at (405) 237-4937 or get in touch online.
There are many causes for a noisy heating and AC system. It’s usually an indication that something is wrong, so don’t hesitate to get in touch with a professional HVAC company if you notice any of the following:
- Squealing or Screeching
Give Interstate a call for prompt attention to your heating and AC system at (405) 237-4937.
For a simple tuneup, you can expect to pay in the range of $100 – 200. But you can expect that investment to pay off. HVAC maintenance with the right HVAC company will help you to:
- Avoid premature system replacement
- Raise your energy efficiency
- Lower your overall repair costs
Those aren’t even all the benefits! Call Interstate Heating and Air Conditioning at (405) 237-4937 to talk to a professional about a plan that will provide you with what you need.
An HVAC repair usually costs about $350-$600 in Midwest City, OK. Some things that can cause the price to fluctuate are:
- The kind of HVAC repair required.
- The level of the HVAC repair.
- The cost for any replacement parts.
Regardless of the repair your HVAC system requires, it is always best to have it addressed right away rather than letting the issue persist. Letting the issue go on too long without repair will typically lead to higher repair costs. To get your HVAC system repaired, contact us today.
for Midwest City, OK
Our Reviews by City
WILLIAM - Midwest City, OK
two thumbs up
Interstate Heat And Air is the best, always professional, and they do a great job.
MICHELE - Midwest City, OK
MARK - Midwest City, OK
Prompt and courteous
DENNIS - Midwest City, OK
RON - Midwest City, OK
Repair man was extremely polite and great to work with.
Very professional and informative
PATRICK - Midwest City, OK
I think the technician should have been wearing a mask for Covid-19 safety reasons.
RITA - Midwest City, OK
Friendly, quick, and polite service. Good explanation of required actions and options.
JOHN - Midwest City, OK
After having four different HVAC businesses provide estimates to replace the AC/heater on a mid-size home I selected Interstate. Turns out to have been a very good decision. Moderately priced for a new Carrier system. Work was scheduled quickly and office kept in contact with me by phone and text to let me know when technicians would arrive. Techs were on time, personable and professional and completed the work in a single day...on the hottest day of the year in OKC. Techs worked efficiently with minimal disruptions to the home and the new system looks great with all of the work appearing tight and clean (the unit itself as well as all the lines and connections). Hauled away all of the old stuff so there was nothing I had to contend with or dispose of myself. A great job all the way around...cannot really think of any improvements. And, of course, the new system is performing superbly.
MARK - Midwest City, OK
Adam took the time to explain things in detail and shared his insights into proposed solutions. Would very much recommend.
Adam is Awsome!
Jessie - Midwest City, OK
Came early! Friendly and thorough! Took extra care and explained all services. He then went over and beyond what he needed to do! I will call Interstate from now on!!!
WILLIAM - Midwest City, OK
Thank You for great service
ROY - Midwest City, OK
I found Joseph Kring to be extremely helpful with my A/C problem and was glad he was willing to look up whether or not my A/C was still under warranty.
TED - Midwest City, OK
Jake provided excellent service in diagnosing and repairing my air conditioning unit. He was very professional, knowledgeable, and answered all my questions. The receptionist was pleasant, and kept me up-to-date on the technician arrival time. I recommend calling Interstate Heating & Air Conditioning for your HVAC needs.
Professional and thorough
Dusty - Midwest City, OK
He did a great job
STEVEN - Midwest City, OK
PAM - Midwest City, OK
Always great service
MICHELE - Midwest City, OK
Everything was great
Great friendly professional service!
KERI - Midwest City, OK
JOSEPH - Midwest City, OK
Brandon was one of the nicest service people who has ever come to my house. if I ever have any problems I want Brandon again
CHARLES - Midwest City, OK
Outstanding service, great arrival timing, great communication and professionalism, great price.
Teresa - Midwest City, OK
Was a little late but got a call from dispatch why which was good customer service. Took less time than anticipated told us there was a couple of vents that were not good so while he was working we went to the store to assist in completing the job. Was very knowledgeable about the job and cared for the condition he left it in. Would do business with interstate again!!
Paul - Midwest City, OK
Adam was running ahead of schedule so he gave us a courtesy call and came by early. Adam is very professional and knowledgeable at his craft. He explained all required services in detail. Thank you!
Huntington - Midwest City, OK
Interstate Heating & Air was very professional and helpful throughout our whole experience with them. They got us scheduled in and came out quickly after reaching out to them for duct cleaning. They did a great job on cleaning the ducts. Highly recommend!
he took care of yhe issue good jo
William - Midwest City, OK
price of labor was a bit hi for a club member
Chi - Midwest City, OK
Isaac was great. I had a lot of questions and he made sure everything was answered in detail.
This is an estimate for replacing an existing mini split, with a new Samsung unit. The line set will be replaced, and a cover will be added to hide the line set on the outside wall going into soffit. Also a pad underneath system to keep it off the ground. System has a 10 year warranty. 1 year labor warranty for installation.
Arrived for blue shield club member AC tune-up. Blower motor amp draw inside is well within range and evaporator coil is clean. Outside at the condenser the capacitor (45.1/45) and contactor check out good. Compressor and fan motor amp draws as well as refrigerant pressures are also good. The unit was cleaned and the filter changed. Overall the unit is working properly with no issues found. Recommendations: 1. Due to the filter being next to the floor it accumulates more dust which is then getting into the system little by little. Recommend either changing the filters more frequently or using better filters I.E. higher than merv 8 rated or filtre 1100. 2. Adding a hard start kit to the unit. This helps the unit start up easier using less power and acts as a secondary capacitor/battery helping decrease the chances of a breakdown.
Came out to call for a mini split not cooling. Customer stated the fan would run sometimes, but it wouldnâ€™t cool. I checked system over and found it low on refrigerant. We had added some refrigerant to the system the previous year, so customer didnâ€™t want to go with that option. I went over repair of the system vs replacement. Customer chose to replace the existing mini split system. I will Email the estimate as an attachment and set up a time to do the installation.
Came out to call for a system not cooling properly. Customer stated that the system is t cooling or blowing any air. I went up on the roof to inspect the system. System is a lennox package unit on the roof of a shopping complex. I did a thorough inspection and found the filters needing to be changed and a blower belt broken. System isnâ€™t getting any air due to the belt being broken. The filters need to be changed as well. I also found what looked to like oil residue near a pressure switch of the system. I tightened nut down to prevent any other refrigerant that may have leaked out. I filled customer in on what was going on with the system and what needed to be done. Customer approved replacing the filters and the blower belt and 2lbs of refrigerant if needed. I picked up filters and blower belt and came back and installed them. Made sure blower belt had correct tension on it. Cycled system on and checked operation. Both stages of cooling came on properly. Second stage that had the po
Upon arrival Drain line was backed up. Relocated drain outside and purged the line with nitrogen, all is clear now. Performed Ac inspection and tuneup. Found a weak capacitor, pitted contactor, and low charge. Replaced the capacitor, contactor, added a hard start kit and 2.5LBS of 410a. Unit likely has a refrigerant leak and leak check was advised. Unit is now working at top shape. I arrived for a non member $99 tune up. I first spoke with the homeowner and found that the system is leaking water and getting the floor wet. We then inspected the complete system found the system to be run low on refrigerant and the capacitor to be reading low and the contactor to be black and pitted. We cleaned the drain line that is included in a tune up and strapped it up and out of the dirt. We then made all, issues aware to the homeowner and we decided to install a compressor savor kit with a turbo capacitor and top off the systems refrigerant charge without a leak search. We did recommend to do a le
Performed preventative maintenance on AC system for customer. Changed filter for customer. Inspected the blower assembly, motor, electrical components, evaporator coil, drain and overall condition of equipment in closet. Cleaned condenser coil thoroughly. Inspected the capacitor, contactor, compressor, fan motor and condenser coil. Checked amps, temperatures and pressures of condenser. System is cooling properly within manufactured specifications at this time.
Performed preventative maintenance on AC. Inspected the blower assembly, motor, electrical components, wiring, capacitors, evaporator coil, compressor, fan motor, amps, temperatures and pressures of condenser. Condenser coil is clean. System is cooling properly within manufactured specifications. Fan motor amps are within range, but a little high. Recommended it be replaced if amps are higher next time.
Performed preventative maintenance on Mini split system. Cleaned condenser coil thoroughly, washed reusable filters. Inspected the electrical components, wiring, amps, temperatures and pressures of condenser. System is cooling properly within manufactured specifications at this time.
Performed preventative maintenance on mini split system. Washed condenser coil thoroughly, and cleaned reusable filters. Checked compressor, electrical components, fan motor, wiring, amps, temperatures and pressures of condenser. System is cooling properly within manufactured specifications at this time.
Came out to perform preventative maintenance on AC system. Customer stated that this system hasnâ€™t been running for a while and couldnâ€™t get it to come on. I checked system over and found the low voltage fuse had been blown. I pulled blown fuse and put a resetable fuse in its place. Went through all the low voltage wiring to find the reason the fuse was blown. After several attempts, I was able to locate that it was blowing because of a minor miswired connection. Condensation pump was wired into the wrong circuit which was causing the fuse to blow. I rewired the circuit and tested the condensation pump and everything worked properly. I checked amps, temperatures and pressures of condenser. Inspected the blower assembly, motor, electrical components, evaporator coil, drain, contactor, capacitor, compressor, fan motor and overall condition of equipment. System is cooling properly within manufactured specifications at this time.
On April 23, 2021 arrive to a new customer nonmember upon arrival I checked the thermostat thermostat operations I didnâ€™t check the blower did amp draws I then went to the condenser checked the components found burned wires and a bad capacitor I recommended the deluxe compressor saver kit and explained what it was customer agreed and said put it on I then did amp draws after installing the compressor saver kit everything is working properly at this time thank you for your business Mike T
On April 22, 2021 I wrote to a Blue Shield club member for a spring tuneup upon arrival I tested thermostat operation I then went to the furnace did amp drawls check blower and capacitor blower bearings are then went to the condenser checked all components disassembled washed reassembled checked system operations everythingâ€˜s working properly at this time thank you for your business Mike T
Came out to give an estimate. Based on discussion I had with the customer. He only wanted to change out the furnace. I gave him a quote to replace the furnace only
On April 8, 2021 arrive to silver club member for AC tuneup upon arrival I checked operations of thermostat I then went to the furnace and checked operation to the furnace did amp draws check blower I then went to the condenser checked the components capacitors hard start kit contactor fan motor did amp drawls I disassemble the condenser washed it reassembled tested operations are things working properly at this time thank you for your business Mike T
On March 6, 2021 arrive to a silver club member for a spring tuneup upon arrival performed amp drawls in the furnace I then went out to the condenser performed amp drawls and condenser checked components check the charge wash the condenser everything is working properly at this time thank you for your business Mike T
On April 6, 2021 I arrive to a silver club member for AC tuneup upon arrival I checked thermostat operations during the unit to cooling I performed amp drawls and tested the furnace and blower I then went out to the condenser I tested components and the charge I disassemble the condenser washed it reassembled test and verify that everything was working properly no issues at this time thank you for your business Mike T
On April 6 2021 I arrived at a previous customer non member for a no cool upon arrival I checked thermostat and found it was working I then located the furnace and seen the float switch was upside down causing the unit not the receive any signal from the thermostat I stood it upright and tested and verified everything is working. I tested both heating and cooling modes everything is working properly at this time Thank you for your business Mike t
On April 1, 2021 I arrive to a Blue Shield customer for AC tuneup upon arrival I checked the furnace did and draws and checked capacitor I then went out to the condenser checked the components on the condenser wash the condenser I was unable to get a 100% accurate charge reading due to it being 43Â° outside but everything is working properly at this time thank you for you business mike T
On March 26 2021 I arrived to a silver club member for a fourth service upon arrival I checked the thermostat and change the batteries with customer supplied batteries I then went to the furnace and checked all components did amp drawls and cleaned Iâ€™ve been tested the system everything checked good unit is working properly at this time. Thank you for continuing to be a customer Mike T
On March 17 2021 I arrived a previous customer non member for a no power to thermostat I arrived and checked system and found that the receptacle in the wall was bad causing the power to short out to the furnace so I replaced the receptacle upon customer agreement and tested I informed them that there filter was bad and recommended replacement and the customer instructed me to change it. Thank you for your business call us if you need anything else Mike, jake
Came out to rerun a 16â€ duct that was kinked in multiple places and starting to make noise. I rerouted the 16â€ duct to elimante the kinks and make for smoother airflow through the duct. Showed customer pictures of what I was fixing and also what itâ€™s supposed to look like. Customer is pleased with the work done and the work we do for him.
1yr part 1yr labor warranty on motor only 1yr part 1yr labor warranty on motor only
Performed preventative maintenance on furnace for customer. Customer changed filters recently. I discussed with customer about a noise that he was hearing from his return duct work on the south end of his home. He stated that the sound only happens after a month or so of changing the filter. We installed the return ductwork a few years ago. I inspected the duct work and found a 16â€ duct to be kinked in two different spots. Which is causing a hinderance in the air flow and increasing the velocity of the air when the filter starts to get dirty. Told customer I would schedule a time to reroute the duct to take out the kinks for better flow of air. I went ahead and inspected the blower assembly, blower motor, electrical components, heat exchanger, burners, flame sensor, ignitor, gas valve, inducer motor and overall condition and operation of furnace. Cleaned flame sensor and brushed dust off the burners and components. Checked thermostat operation, wiring, amps, temperature rise and gas
1yr part 1yr labor warranty on motor only
Found bad induced draft assembly. Will get pricing and availability and follow up.