Give us a call! 405-912-5900
The road to comfort in Moore, OK is Interstate Heating & Air Conditioning. Moore residents can count on Interstate heating and cooling to keep them cool in the summer and warm in the winter. Our certified AC technicians are experts at diagnosing AC problems and completing air conditioner repairs. The same goes for heating repairs and furnace repairs. If you are in need of a new HVAC system, we do that too. One of our comfort advisors an talk to you about the best Air conditioner replacement to fit your needs.
Interstate Heating and Cooling provides:
Read our Moore, OK reviews to see why we are the trusted route for reliable heating and air conditioning services.
Homeowners in the Moore, OK area can expect to pay on average between $4,000 – $8,000 to replace an air conditioning unit, depending on the type of unit and the size of the house. For more information on replacing an air conditioning unit, call Interstate at (405) 912-5900. We offer free price estimates and many options on different units!
There are many different ways homeowners in Moore, OK can lower their energy costs. Here are a few examples:
- Consider investing in a programmable thermostat; the temperature can be programmed to adjust when the homeowner is asleep or gone for work or travel.
- Use ceiling fans, as they can make the temperature feel 6 – 7 degrees lower.
- Weatherstrip doors and windows to make sure that cold air is not escaping.
- A clogged filter can increase energy output by between 5 – 15 percent. Therefore, filters should be changed every few months.
- Employ a certified technician to maintain the air conditioning unit annually. Maintenance keeps a system running efficiently, ultimately saving money in energy costs.
for Moore, OK
Our Reviews by City
LOIS - Moore, OK
Isaac James was Great
KATHY - Moore, OK
He is always professional, courteous and thourough
i’ve only gotten the quote I like Jake
GINNY - Moore, OK
Very personable and very informative
Spring tune up
BARRY - Moore, OK
Jason did a great job. He offered to wash my indoor return duct filters; but since he was pretty busy I did them myself. He also replaced my pan treatment, which was due
PATTY - Moore, OK
Great service, as always!
STACY - Moore, OK
Jason was very professional and arrived in a timely matter! He made sure to wear shoe coverings while inside my house and was very polite! The service was great, as always!
He did a great job
DANNY - Moore, OK
Very thorough. Took pictures of problem and gave options to repair.
JUDY - Moore, OK
Great Service by great people!
R - Moore, OK
BRAD D - Moore, OK
Isaac is a great service tech. Very knowledgeable and extremely customer service driven!
VINCENT - Moore, OK
Isaac was very friendly. He was also thorough with the maintenance.
Reliable company, always available for service of heat/air systems and readily answer any question (s) you may have. Dependable.
SUSAN - Moore, OK
Always professional and knowledgeable about any service you received.
Brandon provided great service
CHRIS - Moore, OK
Brandon was awesome. Very friendly, kind and helpful. Resolved our heating issue, got us up and running quickly!
TRACY - Moore, OK
JEANNE - Moore, OK
Issac James has always been very professional and an awesome technician.
On time, Great service
WILLIAM - Moore, OK
Isaac was polite and efficient
JOSE - Moore, OK
Thanks for all the helpful tips.
CHRISTINA - Moore, OK
Brandon was great! Arrived earlier than expected and answered all our questions.
LOIS - Moore, OK
Jake was polite, efficient and respectful.
Great Service, Very good Serviceman
BILL - Moore, OK
Our system died and the repairman Brandon was very experience and was able to help us with a new system. He listened to what we wanted and took care of everything. Also he lent us a portable heat pump and smaller heater so our house was very comfortable til the new system was in.
Great service and very fast response time!
CHRIS - Moore, OK
Great friendly service
JUDY - Moore, OK
Seasonal Maintenance Check
ROGER - Moore, OK
Issac did a great job in checking our heating units. He was very thorough and very pleasant.
TOM - Moore, OK
Nothing but Professional
JEFFERY - Moore, OK
On July 25, 2021 arrive to a previous customer nonmember upon arrival I agree to the customer customer stated that the unit wasnâ€™t kicking on the outside I had customer go to the thermostat and turn the system on while I was at the condenser fan slowly kicked on the compressor Did not I pulled the disconnect check the capacitor it was dead grabbed a new one got it installed and started the system system kicked on immediately I did amp draws a check to charge everythingâ€™s working like it should thank you for your business Mike t
On July 25, 2021 arrive to a Red shield customer for a no cool upon arrival agreed the customer went to the condensing unit condenser fan motor was not spinning tried to spin it was locked up tight inform the customer they said he got it replace it get a new motor installed just a system operations did it draws and check the charge everythingâ€™s working properly at this time thank you for your business Mike T
One July 25, 2021 arrive to a previous customer nonmember upon arrival agree to the customer customer stated that the outdoor unit would run for a few seconds and turn off went to the outdoor unit open it up check the capacitor capacitor was dead changed it out tested system operations did amp drawls and gave it a quick rinse everything is working properly at this time thank you for your business mike t
Came out to call for a system needing serviced and also check on a noise that the system was making. Customer stated that she hears a squeaking noise sometimes when the system is on. I turned the system on, checked system over and found the filters needing changed, because they were overdue. This was causing an air restriction and could be making a noise due to that. I changed out the filters. I inspected the equipment in the attic and found nothing loose or vibrating at this time. AC needed cleaning, so I cleaned the condenser coil thoroughly. Checked amps, temperatures and pressures of condenser. System was a tad low on refrigerant. Went over the importance of correct charge on a system to cool the home properly. Customer had me add refrigerant. I added 1.1lbs of 410a to get proper charge. Recommend regular maintenance on system. Customer has only owned the home for a year, and should think about having the system properly maintained. I was not able to locate a squeaking noise at thi
Duct cleaning inspection, checked home ductwork for cleaning and found the return okay to clean but not the supplies. The supplies are composed of an older grey Mylar material that eventually deteriorated in the attic heat. At this point, the only way that I can think to proceed is to hav the supply ductwork and the supply plenum replaced with newer material that comes with a lifetime warranty on the craftsmanship and the material. Ductwork includes a new 6 ft metal plenum, dampers and 1 free air balancing. Went over details with customer and they will consider the estimate and get back with us.
On July 22, 2021 arrive to a previous customer nonmember upon arrival customer stated that the unit was not cooling I went to the condensing unit turned it on the fan keep doing but the compressor did not pull the capacitor checked it it was dead grabbed a new one installed it fired up immediately I did amp drawâ€™s check the charge everythingâ€™s good and working properly at this time thank you for your business Mike T
Inspect ductwork and went over options with customer, as existing hard pipe ductwork is somewhat loose and is letting in some attic air due to the insulation around it being deteriorated and the joints not being sealed. Customer is interested in having ductwork replaced in the future, but will just have duct cleaning done for today. Noted that if the ductwork happens to come loose, we will have to charge to repair it and then have to stop the cleaning process. Duct clean 8 supplies and 1 return cavity, add extra to remove over paint on vents and grills. No warranty on duct cleaning, as existing ductwork has gaps letting attic air and insulation in ductwork is deteriorating. Removed vents and grills, and cleaned with dry spinning brush. Carefully Cleaned supplies and return cavities, noting that the central joints seemed to be the most loose on the duct runs. Sprayed in hospital grade disinfectant spray and replaced vents and grills. Also put in fresh 16x25 filter with todayâ€™s cleani
21JUL2021 Jason B Arrived to spring maintenance, spoke with Lois about the systems performance. Changed the filter with an awesome step ladder and replaced thermostat batteries. Cycled system on at the thermostat. Inspected dryer vent coil, blower cabinet, motor and electrical components at the furnace. Verified pressures, contactor, capacitor, fan, and compressor amps. Washed out condenser coils and pad. Straightened up the AC. system is running properly at this time.
Came out to call for a system not cooling properly. Customer stated that the system would not come on at all. They tried changing the batteries in the thermostat and still got nothing. I checked system over and found the control board not getting 24 volts. The transformer is bad. I replaced the transformer and checked wiring, I found the 2 wire to have a short in it. Couldnâ€™t locate the short, and due to wires location, I recommended running a new wire. We are to come back and run a new 24v wire through the attic for customer. Came back out and ran a new condenser wire. Wired into the existing furnace and AC. Cycled system on and my resetable fuse didnâ€™t pop this time. Checked system operations to verify AC is cooling. AC is now cooling properly.
On July 20, 2021 I arrive to a previous customer nonmember upon arrival customer stated that the house wasnâ€™t cooling went to the condenser turned it on it start freezing up immediately check to charge it was at 0Â° vapor saturation inform the customer they said go ahead and add refrigerant where it needs to be I had a 3.57 pounds of our 22 had 15Â° superheat and 10Â° subCalling everything is working properly at this time thank you for your business Mike T
I arrived for a non member no cool call. I inspected the system and spoke with the homeowner and found that his neighbor tried to get the condenser fan motor started by hitch the blades to spin the motor. The top on the condenser is damaged and the fan blade is unbalanced at this time. I found the capacitor to be in readable and not allowing the compressor or condenser fan motor come on. I replaced the capacitor with the homeowners approval and the system came on and ran properly p. The cod fan motor is running at 1.1 amps and its Mac amp draw is not to run at or more than 1.3 amps. I do expect for this condition fan motor to fail. I recommended to repair the condenser fan motor and the blade at this time.
On July 20, 2021 I arrive to a previous customer nonmember upon arrival I greeted the customer they stated that the water tank was leaking I then checked found it was leaking the seal was out picked up a shark bite to replace it but together pressure tested everything water tight there the D pilot and turn the heater on teams heating up everythingâ€˜s good to goThank you for your business Mike T
I arrived for a on member no cool call. I spoke with the homeowner and found that he replaced the fan motor and the capacitor and the outdoor system will not run. I inspected the system and found the main control board to have been burnt due to the thermostat wiring being in poor shape. I recommended to have the thermostat wire re ran through the attic to help prevent this issue agin. We agreed to replace the control board only. I replaced the control board and tested the system in heating and cooling and found no other issues at this time.
On July 19, 2021 I wrote to a previous customer for a no cool that we just installed on arrival agree to the customer and they stay that it wasnâ€™t cooling I went to the condenser he said it wasnâ€™t spinning I open the disconnect when the light was on I change the fuse did amp drawls everythingâ€™s working like it should on the amp drawls tested system operations everything is working properly at this time thank you for your business Mike T
Came out to call for a system not cooling properly. Customer stated that last night the system started blowing room temperature air, and was only getting warmer. They also said the outside unit wasnâ€™t working properly. I found a bad capacitor and a wire burned which tripped the breaker. I reset the breaker went over repair options with customer for capacitor. Customer had me replace the capacitor. I also recommended a hard start kit, to help the compressor out on start up. Customer approved it as well. I added the hard start kit. Cycled system on and checked amps, temperatures and pressures of condenser. Customers service was due so I went ahead and did the maintenance and changed out the filters. System is now cooling properly within manufactured specifications at this time.
Came out to call for an AC leak. Upon arrival the homeowner stated that they think the outside unit is leaking water, because the ground around it is still wet. I checked AC over and found no issues with the actual system. I explained to customer that the AC does create some condensation on hot days, but not enough to keep the surrounding ground damp, unless they had a condensation line ran by the unit, which there wasnâ€™t. I let customer know that it could be a water line that is leaking underground. The neighbor had a French drain put in because of the issue, so itâ€™s likely the leak is underground. I went ahead and changed the filters for customer, and recommended a maintenance plan to continue upkeep on the unit. Though it is only a year old, it should have regular maintenance, especially since itâ€™s a rental property. Thank you for choosing Interstate heating and air! -Isaac
Blue Shield plan ac tune up on 2005 furnace and 2011 AC split system. Spoke with customer and noticed we were out a month prior to add refrigerant. Will double check refrigerant pressures today and check line set and coils for signs of leaks during tune up. Left fresh filters with customer included with blue spp. Wrote down equipment info as best as possible, data plate in AC has worn out, so my best guess is it was replaced the same time as the evaporator coil. Washed condenser thoroughly, and checked inside of coil for signs of oil. Cleaned contactor form excessive mud and dirt buildup. Checked dual capacitor. Went in attic and checked evaporator coil, and mine set and found no signs of oil or leaks. Checked reme halo UVC lamp and it is still functional. Checked blower. Checked ductwork. Some ductwork near supply plenum had come loose on the outer lining. Restrapped it with silver duct tape. Checked drain line which has 2 clean outs on the primary line and confirmed it has proper dra
July 15 2021 Jake K. Interstate heat and air conditioning is a fully licensed and insured company and follow the local and state codes and laws per heating and air conditioning. The system will have a 10 year parts warranty and a 1 year labor warranty. We will remove and hall off the old equipment at no additional charge to the homeowner.
Came out to call for a system not cooling properly. Customer changed out the capacitor and fuses on the system, but the system only cooled for about 2 weeks, then the motor quit, but he got it to work again. Customer believes the condenser fan is going out, but wanted a professional opinion. I checked system over and found all components working. The condenser fan motor is pulling high amp draw and is above the recommended rating (2.3/1.05) on motor. Recommended motor replacement. After discussing with customer about repair needed and pricing, customer decided to hold off on repair at this time.
On July 13, 2021 I arrive to a previous customer nonmember upon arrival I greeted the customer they stated that the unit inside would kick on but the AC wasnâ€™t cooling I went to the air conditioner I checked voltage at the disconnect at 2:40 V I then checked capacitor and contactor nothing to the contactor and capacitor read perfect checked the fuses on the disconnect and found that one of them had popped customer stated that he had a power surge sometimes through the night I did amp drawâ€˜s on the unit during start upAnd it only pulled 10.3 A during start up in for 15 minutes of run time it poured 10.6 A everything is working properly at this time thank you for your business Mike T
Blue shield plan AC service. Spoke with customer and they said home has been cooling okay. Changed filters included with Blue SPP. Washed condenser thoroughly, opening coils and inspecting them, since we had to add refrigerant last Summer AC service. I did not see any obvious spots with a refrigerant leak. Checked dual capacitor, cleaned contactor points and went in attic for inspection. Checked Evaporator coil in place, checked drain line and blower. Cycled system on and checked refrigerant pressure and amp draws. R-22 System is reading 9 degrees of sub cooling and calls for 15. Spoke with customer about refrigerant and doing a major leak search. Customer just wants to add refrigerant for now. Added 1 lb. R-22 to get to 16 degrees of sub cooling. Checked amp draws again and outside delta t. System is working within manufacturer specifications at this time.
Duct cleaning for home with 12 supplies And 1 return. Homeowner is in the process of selling house and wants to provide new homeowner with fresh ducts. Inspected system and it can be cleaned with a level 1 cleaning. Removed vents and grills and cleaned with spinning brush and microfiber cloth. Cleaned return cavity with disinfectant spray and microfiber cloth. Duct cleaned 12 supplies with 3 passes each. Duct cleaned return with 5 passes. Sprayed in hospital grade disinfectant spray and replaced vents and grills. Installed fresh customer supplied filter. Cleaned up excess debris and verified proper thermostat operation. See attached before and after photos of ductwork cleaned.
On July 12, 2021 arrive to a previous customer nonmember upon arrival I greeted the customer and ask them to show me around I went to the thermostat turn the unit on we climbed on the roof check the unit out it was low refrigerant Iâ€™ll let the customer know they said go ahead and gas it up at 4.5 pounds of our 22 to the unit I got the charge where it needs to be everything is working as of right now thank you for your business Mike T
I arrived for a non member system bid replacement. I inspected the system and we compared pricing of other companies and multiple equipment. We bid a 2 ton air conditioner with a 45,000 btu furnace. I offered financing options or a 10% off system replacement if payed in full. This is to replace the equipment only. The system will have a 10 year parts warranty and a 1 year labor warranty.
12JUL2021 Jason B Arrived for spring tune up, and spoke with Leigh about the systems performance. Cycled system on at thermostat. Inspected coil, blower cabinet, motor and all electrical components at the furnace. Inspected pressures, capacitors, fan, and compressor. Washed out condenser coils. Cycled system back on. Left new filters with Homeowner. System is running properly at this time. delta t at 15 69r 54s