Give us a call! 405-912-5900
The road to comfort in Moore, OK is Interstate Heating & Air Conditioning. Moore residents can count on Interstate heating and cooling to keep them cool in the summer and warm in the winter. Our certified AC technicians are experts at diagnosing AC problems and completing air conditioner repairs. The same goes for heating repairs and furnace repairs. If you are in need of a new HVAC system, we do that too. One of our comfort advisors an talk to you about the best Air conditioner replacement to fit your needs.
Interstate Heating and Cooling provides:
Read our Moore, OK reviews to see why we are the trusted route for reliable heating and air conditioning services.
Homeowners in the Moore, OK area can expect to pay on average between $4,000 – $8,000 to replace an air conditioning unit, depending on the type of unit and the size of the house. For more information on replacing an air conditioning unit, call Interstate at (405) 912-5900. We offer free price estimates and many options on different units!
There are many different ways homeowners in Moore, OK can lower their energy costs. Here are a few examples:
- Consider investing in a programmable thermostat; the temperature can be programmed to adjust when the homeowner is asleep or gone for work or travel.
- Use ceiling fans, as they can make the temperature feel 6 – 7 degrees lower.
- Weatherstrip doors and windows to make sure that cold air is not escaping.
- A clogged filter can increase energy output by between 5 – 15 percent. Therefore, filters should be changed every few months.
- Employ a certified technician to maintain the air conditioning unit annually. Maintenance keeps a system running efficiently, ultimately saving money in energy costs.
for Moore, OK
Our Reviews by City
Very thorough. Took pictures of problem and gave options to repair.
JUDY - Moore, OK
Great Service by great people!
R - Moore, OK
BRAD D - Moore, OK
Isaac is a great service tech. Very knowledgeable and extremely customer service driven!
VINCENT - Moore, OK
Isaac was very friendly. He was also thorough with the maintenance.
Reliable company, always available for service of heat/air systems and readily answer any question (s) you may have. Dependable.
SUSAN - Moore, OK
Always professional and knowledgeable about any service you received.
Brandon provided great service
CHRIS - Moore, OK
Brandon was awesome. Very friendly, kind and helpful. Resolved our heating issue, got us up and running quickly!
TRACY - Moore, OK
JEANNE - Moore, OK
Issac James has always been very professional and an awesome technician.
On time, Great service
WILLIAM - Moore, OK
Isaac was polite and efficient
JOSE - Moore, OK
Thanks for all the helpful tips.
CHRISTINA - Moore, OK
Brandon was great! Arrived earlier than expected and answered all our questions.
LOIS - Moore, OK
Jake was polite, efficient and respectful.
Great Service, Very good Serviceman
BILL - Moore, OK
Our system died and the repairman Brandon was very experience and was able to help us with a new system. He listened to what we wanted and took care of everything. Also he lent us a portable heat pump and smaller heater so our house was very comfortable til the new system was in.
Great service and very fast response time!
CHRIS - Moore, OK
Great friendly service
JUDY - Moore, OK
Seasonal Maintenance Check
ROGER - Moore, OK
Issac did a great job in checking our heating units. He was very thorough and very pleasant.
TOM - Moore, OK
Nothing but Professional
JEFFERY - Moore, OK
Lorena - Moore, OK
We were very satisfied with the service from Joseph King on October 19th 2020. He did a real thorough check on our heater. Very nice young man! We will be calling Interstate H&A in the future.
LARRY - Moore, OK
This technician explained it better than anyone we have had.
DARLA - Moore, OK
On time, pleasant, answered all questions, good price.
RETA - Moore, OK
doc - Moore, OK
The person who answered the phone was great. Super friendly and easy to get scheduled. The service person was also friendly and did a good job. AC is still running, so no complaints.
JUDY - Moore, OK
Liam posh is always friendly and able to answer any questions.
ROBERT - Moore, OK
Technician was very professional and courteous. Provided detailed explanation of services
On May 18, 2021 arrive to a silver club member for a spring tuneup upon arrival I checked the thermostat and change the filters customer supplied I then checked the Yvette coil and seen that it was dirty took pictures showed customer a recommended replacement customer agreed gave me the go ahead to get it done clean the coil showed customer when I was done I then checked blower amp drawls And capacitor I then went to the condenser checked capacitor checked contactor checked charge charge of spot one had 12Â° superheat with the piston at the coil I disassembled the condenser I washed it reassembled Jakeâ€™s system operations everythingâ€˜s working properly at this time thank you for your business Mike T
Warranties: 10 year parts 10 year coils 10 year compressor 20 year heat exchanger 1 year labor
Customer wanted quote for blown-in insulation.
On May 18, 2021 I arrive to a silver club member for a spring tuneup upon arrival I checked the thermostat and the thermostat operations batteries were good in it and then went to the furnace I checked the coil open it up showed the customer I then did amp drawls on the furnace checked the blower I change the filter with a customer supplied filter a 16 x 25 x 4 then I went to the condenser I check the charge it had 14Â° sub cooling I checked the components capacitor 45 reading 45 the fan side five equal to five both contactors look really good not fit or burned on either one no loose connections everything is working properly at this time thank you for your business Mike T
I arrived for a non member ac tune up and a no cool. I inspected both systems and found the newer Aaron system to be running in a vacuum. This is the same issue as last summer. The system is leaking refrigerant and is causing the system to not cool. They only wanted to have the system filled at this time. I suggested to have a leak search preformed on the system to find the leaking component and to see what it will take to replace or repair that component. Both systems are running to the best of their abilities at this time.
Performed preventative maintenance on AC system for customer. I inspected the 4â€ ez flex filter, ductwork, blower assembly, motor, electrical components, evaporator coil, drains and overall condition of equipment in attic. Also inspected the fan motor, compressor, contactor, capacitor, condenser coil and operation of condenser. Checked thermostat operation, wiring, amps, temperatures and pressures of condenser. System is operating within manufactured range at this time. I did let customer know that the compressor is starting to get louder, but the amps are within range at this time. Recommended customer plan for replacement in the next couple of years.
I arrived for a silver member ac tune up. I inspected the system and found the evaporator coil to be rusted with oil on the face of the coil. I then I spree outdoor system and found the system to be dirty. I cleaned the system and checked all electrical components and four the systems to be running and 9.8 deg subcooling and the system calls for 13 deg subcooling. I made this aware to to the homeowner and we decided to top the system off at this time. They want to see how the system runs through the summer and we will see how it looks on the next tune up if there are no issues with the system between that time.
Performed preventative maintenance tune up on AC system. Changed customer supplied filter. Inspected blower assembly, motor, capacitor, electrical components, evaporator coil, and the drain. Changed out blower capacitor for customer. Cleaned condenser coil thoroughly. Inspected fan motor, compressor, contactor, capacitor, coil and overall operation of equipment. Checked thermostat operation, wiring, amps, temperatures and pressures of condenser. System is cooling properly within manufactured specifications at this time.
Gave customer estimate for 2 1/2 Full system. Customer was leaning more towards American Standard, but I gave him a quote for American Standard and Carrier based on conversation and customers budget.
Arrived for 2 zone blue club member AC tune-up. Washed both condensers and changed the filters. Refrigerant pressures check out good on both units. Unit for office/entrance area is all pretty clean and blower motor and capacitor check out good. Unit for exam area blower motor checks out good and evaporator coil is clean Concerns: 1. The unit for the break area is very old but is working. Recommend getting a quote on replacement 2. Blower capacitor for exam room unit is reading low 8.4/10 recommend replacing 3. Condenser fan motor for front and office unit is pulling close to max rated amps 1.48/1.52. Keep and ear out for any squeaking from that unit. If some is noticed recommend replacing before it completely goes out. Overall the units are working properly and cooling well
12MAY2021 JB Arrived for spring tune up. Discussed system performance with Karen. Cycled system on at thermostat. Inspected blower motor, amps, coil, and cleanliness of furnace cabinets. Verified integrity of float switches. Found condenser coils to be clean and free from any vegetation or debris. Washed out condenser coils. Inspected electrical components. Hard start,capacitor, and contactor are functioning properly and in within specs. Fan and compressor amps well within manufacturers requirements. System is performing properly at this time.
Arrived for blue club AC tune-up. Checked the blower motor and capacitor on the furnace and everything checks out good. Evaporator is clean. Outside the capacitor and contactor checks out good. Compressor and fan motor amp draws are good as well. Changed both 14x24x1 filters and cleaned the condenser outside. Recommend doing a pan treatment that comes with a 1 year no drain clog warranty. Overall the unit is working properly with no major issues found.
On May 11, 2021 arrive to a new customer nonmember upon arrival customer stated that the house has been getting warm even when the coins gold for I went to the condenser and check the capacitor capacitor was zero on the hermetic side 4.7 on the fan side recommended replacement gave option for a turbo 200 and just regular capacitor customer agreed to do the turbo 200 check system operations everything is working properly at this time thank you for your business Mike T
Arrived for non-member AC tune up. Performed AC tune-up and inspection. Cleaned the condenser and checked all electrical components. Fan motor and compressor capacitor reads good as does the amp draws of the motor. Blower motor capacitor reads good and so did the amp draw. Blower wheel was dirty and the customer elected to clean the blower in place. After all that checked the refrigerant pressures and everything checked out good. Unit is ready for summer.
Dual system under blue shield plan, spoke with customer and they had no issues in the recent snow storm 4 months ago. Washed condensers thoroughly, checked and cleaned out access panels, capacitors and contactors. Supplied filters included with Blue Shield protection plan, customer will replace them self. Checked both system blowers, capacitors, evaporator coilâ€™s and drain lines. Downstairs system drain line seemed to have a small amount of buildup at the coil pan that I removed, but it is draining and making water well. Downstairs system also has a slight vibration from blower and the amps are reading higher than expected. The returns are properly sized, and the blower is reading 11.4/11.8 Amps. There appears to be no damage to the unit at this time, and this is likely a preliminary indicator that the bearings are starting to wear out in the motor. Recommend replacing the motor, the part is under warranty but the labor is not. Left an estimate for customer. Checked refrigerant char
Came out to call. Customer stated that their mini split system wasnâ€™t cooling properly, and wasnâ€™t blowing any air. I checked system over and found that the system needed to be restarted cause it had faulted out. I checked refrigerant and found the system low on refrigerant. Advised customer system has a leak and will most likely need to be recharged again at some point or have a leak search done. Customer had me charge the system to get them up and running for now. I added .7lbs of 410a to get proper charge on mini split. Cleaned washable filters and washed system. The system is cooling properly at this time. They also had another system looked at and they mentioned it to the owner but they didnâ€™t mention it to us. I went ahead and took a look at it. Systems filters are dirty and so are the units. I changed the filters and cleaned the AC system for them. Test and verified that the system is operating properly. I added 1.1lb of 410a to get proper charge on this system. System is
Came out to call for a system not cooling well. Customer knows system has a leak, but just wants to charge the unit with refrigerant at this time. I checked systems refrigerant charge and found it significantly low. Customer approved full amount needed to get it charged. I added 4.2lbs of 410a to get system charge of 10 degrees subcooling. System is about 9 years old, but due to the severity of the leak I recommended system replacement in the near future.
Or May 5, 2021 I arrive to a silver club members for a spring tuneup upon arrival I asked customer to keep the thermostat on to test system operations are then went to the furnace did amp drawls check blower I then went to the condenser checked all the components disassembled washed reassembled and tested system operations everythingâ€™s working properly at this time thank you for your business Mike T
05MAY2021 JB Arrived for spring tune up. Discussed system performance with homeowner, who reported no issues. cycled system on at the thermostat. Inspected coil and blower compartment. Motor is in good shape, and the coil is clean. I found some failing tape on the downflow filter rack. After retaping the seam I brushed out the blower compartment. With customer permission I replaced the all filters. Outside I found the right side of the condenser heavily marked by their dog. While washing it out some of the fins started falling off. Washed the rest of the condenser then let water fall across damaged fins. Restored power to the condenser and checked refrigerant pressures. Coil clean Furnace Blower clean good Blower cabinet clean Amps 4.8/5.6 Ac Clean but Damaged right side Capacitor 41/40 5/5 Fan amps 1 Compressor amps 6.8/ 16.4 System is performing properly at this time.
Performed preventative maintenance on AC for customer. This is a new home and customer stated that everything is covered by the home builder for the first year, but he wanted to have the service done since heâ€™s paying for it. Inspected ductwork, blower assembly, motor, electrical components, evaporator coil, drains and overall condition and operation of equipment. Filter door is missing for filter rack in the attic on the horizontal system. Filter is needing to be changed, and customer will call builder to have it changed. I checked thermostat operation, wiring, amps, temperatures and pressures of condenser. Thermostat was cutting system off at random times and the system is low on refrigerant. Made homeowner aware of the issues going on. Customer is going to contact builder to address all issues that I have found and have them fix it. Thatâ€™s all I was able to do at this time.
Upon arriving at 8:03 AM on May 4, 2021 I cheat thermostat thermostat operations I then went to the furnace change the filter did amp draws J components are then went to the condenser or cheat components did amp drawâ€™s are then check charge I disassembled the system washed it reassembled check system operations everythingâ€™s working properly at this time thank you for your business Mike T
01MAY2021 JB Arrived for blue club tune up. Discussed system performance. Cycled system on at the thermostat. Replaced filters, and inspected coil, blower housing, motor and cage. Verified all electrical components outside at AC. Washed condenser coils. Everything is within proper specs and the system is running properly at this time. Iâ€™ll give you guys a call Monday about that wireless tstat, have a wonderful weekend! Jason
On April 30, 2021 arrive to silver club member for spring tuneup upon arrival I checked thermostat thermostat operations are then went to the furnace did amp drawls check components then I went to the condenser checked components disassembled washed reassembled and then tested system operation everythingâ€™s working properly at this time thank you for your business Mike T
On April 30, 2021 arrive to the Blue Shield club member for a SpringTuneup upon arrival I checked thermostat thermostat operations are then went to the furnace did amp drawls I then went to the condenser checked all system components disassembled washed reassemble Checked system operations everythingâ€™s working properly at this time thank you for your business Mike T
30APR2021 JB Arrived to blue club spring tune up. Spoke with homeowner about system performance. Everything seems tip top. Cycled system on at thermostat. Coil/blower clean and operating smoothly. Washed AC replaced 12x24 filter. Checked all electrical at AC. found capacitor at 55/45 and 7/5 went ahead and swapped it. Fan and compressor amps are in great shape. Change non club filter 14x24x1